The incinerator shall be equipped with a Diesel oil tank which will be supplied with DO from our DO tank located in the
power station. The tank shall be equipped with level switches and proper solenoid valves for automatic filling of
the tank. The tank shall also be equipped with a magnetic level indicator, level switches and proper drain valves,
separate overflow and vent pipes.
Oil-fired multi-stage waste incinerator of pyrolytic type shall be installed complete with interconnecting flue gas
ductwork between the incinerator and the chimney outlet.
The unit shall be manufactured in accordance with the latest ASME code, BS and DIN standards.
The waste disposal shall be environmentally acceptable and the incineration emission shall comply with the admissible
emission limits (international EC-Standards). The waste
shall be totally burnt and the content of un burnt organic matter of the ash shall not exceed 3%.
The unit shall allow for at least 2.0 seconds retention period.
1.2 QUALITY ASSURANCE:
- Coordinate the entire assembly of incinerator, stack, controls, fuel supply.
- Provide written certification that the entire assembly has been coordinated to achieve the required performance
and to provide the required attributes.
- Equipment, installation, and operation shall conform to NFPA 82. Where conflicts exist between NFPA 82 and this
specification, this specification shall govern.
- Submit in accordance with Section 01 33 23, SHOP DRAWINGS, PRODUCT DATA, AND SAMPLES.
- Arrangement, description of construction, and outline drawings of incinerator and accessories showing
clearances and dimensions.
- Predicted performance including burn time based on waste composition specified.
- Calculation of secondary chamber retention time.